About Climate Change Services
Climate Change Services are an Air Conditioning & Refrigeration Specialist Company. We aim to provide a personal service to Domestic, Commercial & Industrial customers. Ensuring value for money and quality of workmanship.
With experience of over 15 years in the industry on a range of applications and projects we aim to meet any requirements.
Climate Change Services are a REFCOM / FGAS accredited Company, our engineers are professionals that are trained to the industry standard.
What We Do
Our services include:
- Design and Installation of systems
- Commissioning and De-Commissioning
- Callout Service, Repair and Maintenance of all types of Air Conditioning, Refrigeration, De-Humidification Compressed Air Driers and Ventilation Equipment.
- We also provide portable Air Conditioning systems for sale and hire purposes.
A free site survey is provided for Installation enquiries.
What people say…
Tuesday 26th of February 2019
Call out to a Beer cellar system. "HI-TEMP" We found that the TEV was leaking / installed poorly by others. Re-flared, pressure tested and 're commissioned the system the same day. Very happy customer!
Tuesday 12th of February 2019
We discovered poor lagging and insulation on a branch controller box. The condensation was dripping onto a cable tray, then finding it's way into a light fitting and tripping an electrical circuit at the distribution board. Once correctly insulated the problem was resolved.
Wednesday 6th of February 2019
Air Conditioning and Refrigeration Specialist Maintenance being carried out at a local Brewery
Wednesday 30th of January 2019
Condensate pumps can cause problems when not maintained correctly. The tank pump shown was not maintained often causing it to fail and leak over 5ltrs of condensate through a wall, damaging the decoration and plasterwork. We sourced a replacement and repaired within 24hrs.
Friday 25th of January 2019
Trace Gas (Hydrogen) pressure testing and leak finding with bubble. After reports of poor cooling, we investigated a chiller system. The system had very low levels of refrigerant left in the circuit. We used Trace Gas with a specialist hydrogen detector to find the leak. You can see in the image that the leak was small, but traced to the T.E.V. We repaired the leak and the got the system up and running with limited downtime.
Tuesday 15th of January 2019
We are currently in the process of repairing a Chiller with a refrigerant leak.
The leak was detected whilst pressure testing using OFN. We then removed the faulty pipework and replaced with new
Wednesday 9th of January 2019
Maintenance in progress.
You can see the condensor coil is heavily soiled causing poor airflow and heat exchange.
Chemical cleaning is part of the process of our maintenance services.
Thursday 20th of December 2018
MHI 5 KW Server Split System
Saturday 8th of December 2018
2 x MHI Multisplit Domestic Installations completed
Sunday 2nd of December 2018
We worked on a system that was installed in 1995 this week, running on R22 refrigerant.
After performing a maintenance and an F-GAS Leak check it was proven that no leak was present.
The system was working extremely well with decent running pressures.
This proves that regular maintenance of equipment keeps the systems up to scratch, keeping coils clear preventing airflow issues.
We aim to provide an excellent service.
Monday 26th of November 2018
We install Inoac trunking to disguise pipework and services on domestic installations.
Saturday 17th of November 2018
A replacement was carried out to a vandalised cage protecting a unit.
The replacement cage(s) are now reinforced through the middle to counter the vandalism. Much improved.
Sunday 11th of November 2018
We attended a site with over 60 Floormounted Evaporators on VRV systems. The equipment was found to have condensate pumps installed to each evaporator, but poorly installed under the floor with no access to maintain. Maintenance is an integral part of FGAS leak finding, but also keeping the systems healthy and highlighting any potential issues arising.
Sunday 4th of November 2018
10 kw Fujitsu wall mounted Split system Installation (R410a)
Sunday 4th of November 2018
Another successful Installation.
10 kw Fujitsu wall mounted Split system. (R410a)
Thursday 25th of October 2018
After the record breaking Summer heatwave, now is the time to book in preventative maintenance to ensure FGAS compatibility and energy efficiency.
Friday 19th of October 2018
Daikin Split and Fujitsu Multisplit installation
“Excellent work and really personable and trustworthy. Did not try to sell me a new unit as agreed the 13 year old air conditioner was in great condition. Highly recommend.”
“Chris was absolutely brilliant, I couldn’t commend him more. He came for a quick site visit the day after I made the first inquiry and was able to take a quick look and evaluation of what was needed, clearly explain to me the options and how much it would cost. He was happy to answer some follow-up questions by email which was replied to the same day. Only a few days later, as soon as the parts were ready, everything was installed to top standard, fully tested, no mess and running perfectly and Chris was happy to explain everything as he went. Always with a smile and happy to help!”
“First class workmanship and service. We were kept informed all the way. Chris is a gentleman and we would not hesitate to recommend him to anyone wanting air conditioning put in.”
“Chris provided an excellent and professional service to a high standard. Can’t fault him at all for anything and would fully recommend to anyone looking for air conditioning.”
“Chris did an excellent, thorough job. He arrived exactly on time and was very friendly. I would highly recommend him.”
“Came on time, with appropriate materials and worked consistently hard throughout the whole day. Had organised timely arrival of new units and removal of salvage – ran like clockwork. Left all areas of work spotlessly tidy, even did the vacuuming for me!”
“Chris was knowledgeable and professional, gave good advice and quoted competitively. Job took half a day. He carried out the work cleanly and efficiently to a very high standard. Excellent, friendly service. Wouldn’t hesitate to call on him again. Highly recommended.”
“What a great guy! We ordered a AC unit online for our which said it could be installed by a competent DIYer but after reading the small print we needed a qualified person! I rang Chris in the morning who was incredibly helpful and understanding. After sending a few photos he fitted us in that afternoon. His workmanship was spot on all the cabling was left neat and tidy and its great to see someone enjoying there work so much by whistling through the whole job. He even went through the controls with me with a product he didn’t supply to save me reading the instructions! Would use and recommend…”
“Extremely happy with Chris at Climate Change. Polite, on time, kept us informed of progress, left no mess. Would definitely recommend and would use again.”
“Absolutely over the moon with the service we have had from Chris / Climate Change Services. The quote we received from CC was the most competitive and the quality of the workmanship was second to none. The system that has been installed is to control the temperature of an external home cinema room and is working lovely to keep the perfect temperature in the room. It was a very hassle free experience where no marks were left on my walls or on the carpet. Chris has even called up a few time to make sure everything is running smoothly. I couldn’t recommend him more highly. Thanks once again.”
“Chris was very flexible in his approach. Making sure that he understood what we were trying to do at all times in our new premises. Chris also went above and beyond in cleaning equipment that he had not provided. Friendly approach, but clearly knows his product. Highly recommend on both price and service.”
“Very pleased with the work that was carried out. Would definitely recommend.”